Payment & Shipping Terms:
|Power:||30w 45w 60w 75w 100w||Voltage:||100-277V 347V|
|Luminous Efficiency:||120lm/W||Colour(CCT):||3000K, 4000K, 5000K, 6000K|
|LED Type:||SMD3030 With Lm80 Report||CRI:||Ra>70|
|Power Factor:||>0.95||Beam Angle:||120°|
|Body Colour:||Black / Gray||IP Grade:||IP65|
|Material:||Die-cast Aluminum, Pc Lens, Silicone Ring||HS Code:||9405409000|
UL/Dlc Listed 45W 60W LED Canopy Light for Gas Station/Stadium/Metro Station/Supermarket Lighting
LED Canopy Light owns the smallest size in the market, 265*265*95mm, it is the most cost effective led canopy light in the market.
The heavy-duty die cast aluminum heatsink can provide strong resistance to corrosion and weathering, so that the led canopy can
be used in wet location.There are 3 ways for easy installation, mount with J-box or 1/2" conduit, pendant install with 3/4" conduit
Input Voltage: AC100-277V/347 50/60Hz
Power: 30w 45w 60w 75w 100w
CCT: WW(3000K), NW(4000K), DW(5000K), CW(6000K)
Light Source: lumileds 3030SMD LED
Certification: UL DLC CE, RoHS
Description: LED canopy lights with smart fin shape heat sink, better heat dissipation and longer life span, good quality with the use of MeanWell driver and Lumileds chips.
|Power||Input Voltage||Lumious Flux(lm)||MH/HPS Equivalent||Product Dimension||Luminous Efficiency|
1. Surface Mounted with J-box
1.1Loosen the screw on side of the light, removing the bracket from Canopy light by pulling it out slightly, just leaving the ring on bracket.
1.2 Fix the bracket on J-box, and put the wire through the central hole for wiring.
1.3. Attach the Canopy light with bracket by putting the ring on clips again. Connect the Black wire for Line, White for Neutral, Yellow Green for Ground.
1.4.Slide the Canopy lights into bracket, and secure the screw on side of the light to prevent the light from sliding out from the bracket. Installation done.
2. Pendent with 3/4 inch Conduit
2.1. Loosen the screw on side of the light, removing the bracket from Canopy light by pulling it slightly out, just leaving the ring on bracket. ( See the Step 1 above)
2.2. Connect the wires threaded from conduit and Canopy, Black wire for Line, White for Neutral, Yellow Green for Ground.
2.3. Screw the Conduit into the hole on top of Canopy light. Installation done.
3. Surface mount
3.1. Remove the lens and metal plate by unscrewing the screws.
3.2 2.Drill 4 holes on edge of fixture and fix it on the ceiling with using appropriate screws. Cut off the wires through from 3/4'' hole and plug the hole with provided Plug.
3.3. Remove 1/2" plug from direction you intend to feed conduit.
3.4. Disconnect the wires came from 3/4'' hole and connect the wires came from 1/2'' conduit with power supply . (White for Neutral, Black for Line, Yellow Green/Green for Ground)
3.5. Replace the metal plate and the lens, make sure no wires are pinched when replacing parts.
Factories, Yards, Gas station, Gymnasiums, Wineries, Schools/government buildings, Exhibition, Hospitals, Applications in Storage Areas, Garages, Canopies, Warehouses, Hotel Canopies, Entry Ways, Security Lighting etc.
Switch off power of the mains supply or respectively of the connection lead before doing any works.
Assembly must not damage or destroy conducting paths.
Make sure that the product is mounted on a stable, even and tilt-fixed background.
The complete installation must be done by an electrical expert who is familiar with the valid directives.
Stability TEST: make sure 100% of the lamps be aging test at least 48hours
Lighting TEST: make sure 100% of the lamps be lighted before packing
Drop TEST: make sure every single light have been well protected by box
Mobile: 0086-180 0253 2737
Please feel free to send us your inquiry, We are at your service any time!